Fan on the Pull Side of the Filter
Below is the sort of filter housing I'm talking about. I'm guessing it is called a filter housing but I don't know for sure. In the picture it's the big metal container on stilts above the skip.
In fact, the system in the picture may have the fan on the pull side. I say this because the ducting from the fan enters the filter housing at the top instead of the bottom. Can anyone make out if the fan is on the pull or the push side of the filter housing?
From contributor K:
The primary advantage of putting the fan on the clean/pull side of a system is fan efficiency. You are able to use a clean air fan, which does not need to be concerned with self-cleaning features. We can use the most efficient blade designs, which do not offer self-cleaning characteristics, however the energy savings is dramatic. In terms of efficiency, it's not uncommon to see 25-30% difference. With dirty air/push fans, the blades must be radial to the wheel hub, so that no buildup occurs on the back/non-air side of blade. This design is not as efficient as a backwardly inclined/curved wheel.
Other advantages for clean air fan include quieter operation and reintroduction of clean air back into facility, eliminating need for makeup air to avoid negative building space (although this has become a hot spot with OSHA/NFPA regulations as relates to fire hazards - check with local authorities having jurisdiction).
Would you like to add information to this article?
Interested in writing or submitting an article?
Have a question about this article?
Have you reviewed the related Knowledge Base areas below?