Insulation Value of Wood
Wood's R-value is not trivial, but air leaks and bypasses often dominate the equation. April 11, 2008
I have a customer that is going to finish off the inside of a pole barn with 5 inch thick poplar and he would like to know its R value. I told him that I don't think it will be very much. He already has 2'' thick pink foam board and wants this to protect the foam and insulate. Can anybody help me give him an answer?
(Sawing and Drying Forum)
From Professor Gene Wengert, forum technical advisor:
The link below has the R-value of 1.1 per inch of thickness for yellow poplar at 12% MC (Chapter 3, page 3-19). So, for 5" material, he would have 5.5 R value... not bad at all. Wood is a good insulator indeed.
The real problem with R-values in general is that air leaks and window/door leaks often result in more heat loss than the wall itself. In the case of a barn, the floor and roof can lose many times more heat than the walls. That is why we use perimeter insulation around the foundation and double the insulation in a roof.
(Special note: In a kiln with good air circulation, the extra roof insulation is not needed; it is only when interior hot air will rise to the ceiling that the extra insulation is beneficial in reducing heat loss.)
Would you like to add information to this article?
Interested in writing or submitting an article?
Have a question about this article?
Have you reviewed the related Knowledge Base areas below?
All rights reserved. No part of this publication may be reproduced in
any manner without permission of the Editor.
Review WOODWEB's Copyright Policy.
The editors, writers, and staff at WOODWEB try to promote safe practices.
What is safe for one woodworker under certain conditions may not be safe
for others in different circumstances. Readers should undertake the use
of materials and methods discussed at WOODWEB after considerate evaluation,
and at their own risk.
335 Bedell Road
Montrose, PA 18801
Copyright © 1996-2015 - WOODWEB ® Inc.