Variable-Speed Controls and Explosion-Proof Fans
Using a variable-speed controller likely voids the explosion-proof rating on a fan. August 14, 2007
I recently purchased a 20 inch Jenny variable speed explosion-proof fan. I have done some electrical myself, and was wondering if anyone out there has hooked up their own variable speed model and could offer some assistance.
From contributor L:
Usually an explosion-proof fan cannot be variable. When the fans are operated slower than spec speed, the temperature rises above the tolerance that keeps them within the explosion-proof rating.
From contributor D:
I mean this in the nicest way. When it comes to electrical work, if you have to ask, you should probably not be doing it. We all have our limits of expertise. The difference could be as simple as a call to an electrician or a call to the coroner. Your money or your life?
From the original questioner:
Thanks for your concern, but I think it's more dangerous not to ask. I called Jenny and got tech support, black (hot) to yellow line wire from motor neutral (white in line with variable speed switch), ground (green to earth ground). I already tested, works great. Also, why would they sell a variable speed version if it were not intended to function that way?
From contributor L:
You can put a VS unit on the explosion proof fan and it will function properly. It will no longer be classified as an explosion proof fan because the case can rise above the threshold temperature.
Would you like to add information to this article?
Interested in writing or submitting an article?
Have a question about this article?
Have you reviewed the related Knowledge Base areas below?
KnowledgeBase: Knowledge Base
KnowledgeBase: Dust Collection, Safety, Plant Management
KnowledgeBase: Dust Collection, Safety, Plant Management: Safety Equipment
KnowledgeBase: Finishing: General Wood Finishing
All rights reserved. No part of this publication may be reproduced in
any manner without permission of the Editor.
Review WOODWEB's Copyright Policy.
The editors, writers, and staff at WOODWEB try to promote safe practices.
What is safe for one woodworker under certain conditions may not be safe
for others in different circumstances. Readers should undertake the use
of materials and methods discussed at WOODWEB after considerate evaluation,
and at their own risk.
335 Bedell Road
Montrose, PA 18801
Copyright © 1996-2019 - WOODWEB ® Inc.