Explosion proof lighting
What type of lights should be used in your spray booth? May 19, 2003
I am in the process of setting up a spray booth in my shop and want to make my fluorescent lighting safe. Can I do this without spending upwards of $400 per fixture? My inclination is to build a gasketed box of some variety. Some say not too worry about the lights and others say the risk is high.
From contributor J:
A true 4 tube x/p light fixture is less than 1900. You should be able to get a class one div 2, typically called sealed and gasketed, for about 300 bucks.
That said, you are on the right track with mounting the fixture above the roof of the booth and putting glass in the opening and sealing with a non-silicon based caulk.
We did our lights in a box of double-walled fire rated sheetrock with a gasketed glass cover. There was also a switch box with a button that turned off electricity to lamp socket each time glass was removed. This was for upgrading an existing location to code, not for building new. You should check with local codes to see what is required in your area.
From contributor J:
Codes can be a real pain the ass. Paint rooms are class one, div one. Spray booths, three sided and four sided, can use booth class one, div 2 lights, sealed and gasket within 5 feet of the opening and regular open lights in the rest of the opening.
In my shop I use the book my fire marshal uses, nfpa 33.
Grainger sells dust-proof gasket sealed fixtures - eight footers. Run wire in plastic conduit. Each end has a thread. My whole shop has these. Very safe but not legal.
Would you like to add information to this article?
Interested in writing or submitting an article?
Have a question about this article?
Have you reviewed the related Knowledge Base areas below?
KnowledgeBase: Dust Collection, Safety, Plant Management
KnowledgeBase: Dust Collection, Safety, Plant Management: Safety Equipment
KnowledgeBase: Finishing: General Wood Finishing
KnowledgeBase: Finishing: High Speed Production
KnowledgeBase: Finishing: Refinishing
All rights reserved. No part of this publication may be reproduced in
any manner without permission of the Editor.
Review WOODWEB's Copyright Policy.
The editors, writers, and staff at WOODWEB try to promote safe practices.
What is safe for one woodworker under certain conditions may not be safe
for others in different circumstances. Readers should undertake the use
of materials and methods discussed at WOODWEB after considerate evaluation,
and at their own risk.
335 Bedell Road
Montrose, PA 18801
Copyright © 1996-2019 - WOODWEB ® Inc.