High Speed Abort Gate for Dust Collection System
This component activates to divert the duct airflow out of the building for fire safety in case of an explosion. October 20, 2013
Our insurance loss control was out last week and we got a clean bill except for the new DC we are installing. He is saying we need a high speed abort gate on the return air. Anyone have one or know what they are all about? I searched google and it looks like a huge monster!
(Dust Collection and Safety Equipment Forum)
From Curt Corum, forum technical advisor:
When required, they would be located on the return air duct from dust collector and prior to dust collector. In the event of a bag house explosion, diverts to outside instead of back into the building. Pyroguard has them from 4" diameter to 60" diameter.
From contributor D:
They are cost effective and are located on the return air duct after the dust collector to meet NFPA 64 requirements for fire. Usually these are tied to a spark detection system which we [Kraemer Tool] also supply to operate the abort gate if a spark is detected in the duct that is travelling towards the dust collector.
Would you like to add information to this article?
Interested in writing or submitting an article?
Have a question about this article?
Have you reviewed the related Knowledge Base areas below?
KnowledgeBase: Knowledge Base
KnowledgeBase: Dust Collection, Safety, Plant Management
KnowledgeBase: Dust Collection, Safety, Plant Management: Safety Equipment
All rights reserved. No part of this publication may be reproduced in
any manner without permission of the Editor.
Review WOODWEB's Copyright Policy.
The editors, writers, and staff at WOODWEB try to promote safe practices.
What is safe for one woodworker under certain conditions may not be safe
for others in different circumstances. Readers should undertake the use
of materials and methods discussed at WOODWEB after considerate evaluation,
and at their own risk.
335 Bedell Road
Montrose, PA 18801
Copyright © 1996-2017 - WOODWEB ® Inc.