Waterborne Formulas and Spray Booth Fire Codes
From contributor D:
Every location may have different rules, but I just met with the Fire Marshall at a shop I am buying that is too old to comply with current code for the existing booth. The cost to bring it up to code would be too high for me to justify right now. The FM said if I only spray waterbornes, the booth is fine as is. If you spray 1% of solvent stuff though, you would still have to comply with all codes. Each area will vary though.
From contributor M:
The answer is… it depends. The most frequently enforced standard for spray booths is NFPA 33 Standard for Spray Application Using Flammable or Combustible Materials. This document is referenced in the International Fire Code and was the basis of the OSHA rules for spray finishing. Chapter 1 of NFPA 33 covers the scope, purpose and application of the standard. Section 1.1.3 states that this “standard shall also apply to spray application of water-borne, water-based, and water-reducible materials that contain flammable or combustible liquids or that produce combustible deposits or residues.”
You can check with the manufacturer or the MSDS sheets for the materials you are spraying to see if the material is flammable or combustible in either the liquid (as sprayed) or dried state (deposits and residues). There are paints that contain no solvent, but the dried overspray can still present a fire hazard.
I couldn’t agree more with contributor J - it is always best to meet with your local authority (fire marshal, building inspector, insurance carrier, etc.) to determine the requirements for the installation and operation of a paint spray booth.
Would you like to add information to this article?
Interested in writing or submitting an article?
Have a question about this article?
Have you reviewed the related Knowledge Base areas below?